Become Our Distributor
If you are interested in becoming our distributors or Resellers, please fill-in the form below and submit to us.Our Sales team will contact you with 24 hours.
FREQUENTLY ASKED QUESTIONS
JUST FIND YOUR MAINTENANCE TIPS BELOW
Reason: It may be cool water not enough; or cool load low; or failure occurred at throttle orifice; or heat transfer at heat transfer tube of evaporator bad for the pollution like furring; or lack of refrigerant.
Solution: Check the cool water circuit and refill the cool water to rated volume; or check the rated temperature at auto on/off device; or check if expand throttle is blocked; or clean the heat transfer tube; or fill the refrigerant to needed volume.
What to do when condensing pressure is too high?
Reason: It may be cooling water not enough; or capacity of cooling tower reduced; or temperature of cool water too high; or cooling capacity too high to increase the load at condenser; or non condensed gas exist; or heat transfer at condensing tube bad for the pollution like furring.
Solution: Check the cool water circuit and adjust it to rated current flow; or check cooling tower and expand throttle etc. to lower (or rise) the temperature of cool water to rated temperature as soon as possible; or get rid of non condensed gas; or clean the tube.
What to do when the difference of oil pressure is too low?
Reason: It may be oil filter blocked; or oil pressure adjusting valve (gate gurgle valve) opened too wide; or outlet oil at oil pump decreased; or bearing abrades; or failure occurred at oil pressure meter (or sensor); or too many refrigerant mixed into lubricating oil (oil pressure is too low for oil bubbles when starting).
Solution: Change the core of oil filter; or tighten the oil pressure adjusting valve so that the oil pressure rise to rated pressure; or disassembly to check; or change the bearing; or check oil pressure meter, reset the pressure sensor and change it when necessary; or do apply the oil heater when cooler stops to maintain rated oil temperature (check if wire of oil heater is breaking, and if the set temperature for oil heater to heat is correct).
What to do when cool water is subcool?
Reason: It may be cool water not enough; or cool load low
Solution: Check the cool water circuit and refill cool water to rated volume; or wait for cool load rise.
Over load at oil pump
Reason: It may be oil pump broken; or resistance at oil circuit too great.
Solution: Disassembly the oil pump to check; or check the oil circuit system like oil filter and other components, change them when necessary.
What to do when oil temperature is too high?
Reason: It may be cooling capacity of oil cooler lowered; or refrigerant supply for cooling oil cooler not enough for refrigerant filtering net is blocked; or bearing abrades.
Solution: Adjust oil temperature adjusting valve; or clean refrigerant filtering net; or disassembly to repair or change bearing.
What to do when water failure occur?
Reason: It may be cooling water not enough; or failure at differential meter
Solution: Check cool water pump and cool water circuit and adjust to normal flow volume; or check and repair differential meter.
What to do when winding for main motor is superheat?
Reason: It may be power phase voltage unbalance; or voltage drop at power cord large; or operating with ultra low head; or refrigerant supply for cooling main motor not enough for refrigerant filtering net is blocked.
Solution: Take measures to make power phase voltage balance; or take measures to lower voltage drop at power circuit; or clean the refrigerant filter net.
The LCD frame case is not fixed well
Contact the service center
The outdoor environment temperature is lower than -5℃
Affect the function of air conditioner
Heat pharmaceutical leaks
Contact service center
Room temperature is set too low to heat———————————————————————
Increase the set temperature
Doors or windows aren’t close well———————————————————————
Close the door or window to preserve cool (heat)
Air filter is dirty or blocked
Clean filter to improve airflow
Tighten the screw
There are foreign objects on the unit
Remove the foreign objects
Bracket of the unit is not installed steadily————————————————————————
Fix the bracket or reinstall it
Unit is not placed well
Adjust the location of the units
Compressor is not installed well, or the floor stand is not firm enough——————————————————————————————————————
Check if the floor stand is firm
Change integrated modular CPU
Cool joint or breakage at manostat 7806
Change manostat 7806
Crystal oscillator or resetting circuit element is broken———————————————————————————————
Commutate diode is broken
Change commutate diode
Transformer is broken
Change the transformer
Blow of the fuse
Change wireless remote controller
Breakage or bad connecting of the receiving terminal
Change receiving terminal or adjust connecting wire of receiving terminal
Receiving terminal is loose
Adjust the receiving terminal
Check if the contact points are connected by multimeter when the compressor is not over heated, if it isn’t connecting, change protector
Compressor cannot run smoothly, crankshaft jammed or breakage of discharge valve
Capillary is blocked and inspiration temperature increases———————————————
Refrigerant is not enough or too much
Adjust the amount of refrigerant
Change the battery
Wrong wire connection
Reconnect the wire
The main On/Off switch is broken
Change the main On/Off switch
Compressor capacitor is broken
Change compressor voltage
Set temperature of temperature controller is too high or temperature controller is broken
Decrease the set temperature of temperature controller or change the temperature controller
NEW PRODUCTS RELEASED
Check out the latest and greatest products released from DELTA